|View single post by applianceman18007260692|
|Posted: Mon Oct 1st, 2007 04:20 pm||
|if that gas valve aint opening it could be a faulty burner to ground on the module(remove corrosion from terminals)
contaminated sensor may be the culprit(Shine the sensor with sand cloth)
draft inducer fan pressure not adequate(check the cage)
draft inducer bellows switch may be bad(blow out the cobwebs)
or it could be the gas valve itself is haywire(continuity)
one of the roll out switchs might be open(4 each switch must be closed)
a roll out will pop open when a rusty burner does not ignite properly
making the flame roll out of the cumbustion chamber.
Attachment: sensor1.jpg (Downloaded 56 times)
"May the hinges of our friendship never grow rusty"
-old Irish saying
Buy me a Beer: http://web.me.com/zenzoidman/applianceman18007260692/