|View single post by Trying to help|
|Posted: Sun Jun 25th, 2006 03:16 am||
Trying to help
|LOVE THE GRAPHICS!!! Pegi led you to the water and even held your head under a little.
G-I.P .5 P.S.I.
3.03/3.3 V.A.C. Voltage need to the gas valve. (if you do not have an amp meter)
3.3/3.6 AMP . Amp range needed to open valve.
As long as voltage was within specs, approx. 112VAC or higher, your igniter is weak. Click the link above and get one on the way. Great job, proved it without a doubt! Did I mention I love the graphics!!
Last edited on Sun Jun 25th, 2006 03:18 am by Trying to help
Need parts? Call our Parts Department now! 877-803-7957